Boiler was not igniting and making strange noises. The customer advised that they had no heating or hot water. The boiler had not been serviced for 3 years.
- Norris Rd, Sale M33 3GS
- Worcester Bosch Greenstar Junior
After close inspection it was found that the primary heat exchanger was choked up. The condensate trap was also blocked.
We carried a full strip and service on the boiler and cleaned all the components from contamination. The boiler was repaired and checked for correct operation and was working fine.
A visual inspection and check of the boiler was carried out, followed by a gas safety check and a flue gas analysis.
- No Hot Water from Boiler in Sale M33 7XF
- Boiler Malfunctioning with Hot Water in Sale M33 7TS
- Boiler Losing Pressure and Required Topping Up in Sale M33 2LT
- Boiler Leaking in Bungalow in Sale M33 3DF
- Drip in Viesman Vitodens Combi Boiler Repaired