The customer called to say that their boiler was losing pressure, and they had to keep topping the system pressure up with water.
We were able to diagnose the issue over the phone.
- Dane Rd, Sale M33 2LT
- Detached House
- Worcester Bosch CDI Classic
The boiler was losing pressure due to a failed expansion vessel. We explained that the failure was probably due to the system water being contaminated.
Removed the boiler from the wall which involved disconnecting the flue, electrics and all connections on the boiler.
Fitted a new expansion vessel and PRV (pressure relief valve) as a precautionary measure.
A visual inspection and check of the boiler was carried out, followed by a gas safety check and a flue gas analysis.
Manchester Plumbing and Heating (Sale) boiler repair is extremely reliable with our excellent reputation covering the whole Greater Manchester area. We have many years of qualified engineering expertise and experience to back it up. On-going boiler servicing and maintenance ensures the energy efficiency and longevity of your home’s heating system.
- Boiler Leaking in Bungalow in Sale M33 3DF
- Boiler Malfunctioning with Hot Water in Sale M33 7TS
- No Hot Water from Boiler in Sale M33 7XF
- Valiant Boiler Gurgling and Cut Out in Sale M33 7UE