Contacted us for a boiler service on Vaillant Eco Tec Pro 28.
- Clarendon Rd, Sale M33 2DU
Removed the fan and burner case to find that the burner was heavily contaminated with debris. Cleaned with a liquid chemical and brushed clean. Flushed with clean water.
Cleaned out the condensate trap which was heavily contaminated. Cleaned the ignition electrodes and air dusted the fan and all visual components.
A visual inspection and check of the boiler was carried out, followed by a gas safety check and a flue gas analysis.
- Worcester Bosch CDI Annual Service in Sale M33 5QT
- Urgent Service on Baxi 836 Boiler in Sale M33 4AT
- Overdue Boiler Service for Baxi Combi in Sale M33 4RZ
- Vaillant Eco Tec Pro Annual Service in Sale M33 6GQ
- Annual Boiler Service on Vaillant Eco Tec in Sale M33 3AJ