Customer rang to say that there was a small drip coming from the right hand side underneath the boiler.
- Wynyard Close, Sale M33 3JT
- Semi Detached
- Viesman Vitodens 100-W 35Kw Combi Boiler
Upon inspection we found that the auto air vent was leaking contaminated water from the central heating system.
We replaced the auto air vent and carried out a full system power flush to clean all the central heating pipework, boiler and radiators and the system was dosed with a premium anti corrosion inhibitor.
We recommended fitting a magnetic filter to protect the boiler and system in the future.
A visual inspection and check of the boiler repair was carried out, followed by a gas safety check and a flue gas analysis.
- Ideal Logic Repaired with Loud Noises When Running on Demand
- Repair on Worcester CDI with Heat but No Hot Water
- Boiler Ignition Problems & Noises in Sale
- Ideal Logic Boiler Working Intermittently in Sale
- Boiler Repair Call Out for Loud Noise in Ideal Logic