Baxi Boiler not working correctly and the customer was concerned that it was quite noisy when running.
- Glebelands Road, Sale M33 6LQ
- Mid Terrace
- Baxi Duo Tec
The boiler was noisy when running so we checked the following:
- Ignition electrodes
- Ignition leads
- Gas valve etc
Upon inspection we found that the condensate trap was full with debris. This caused a build up of material in the bottom of the heat exchanger and cleaned this out thoroughly.
The condensate trap was removed, cleaned and the seals were lubricated with silicone and the ignition electrodes were also cleaned.
We ran the boiler and carried out a flue gas analysis.
The boiler seemed to be working correctly with a final visual inspection and check of the boiler repairs carried out, followed by a gas safety check and a flue gas analysis.
Reliable Baxi Boiler Repairs From Trusted Experts! Manchester Plumbing and Heating (Sale) offers comprehensive Baxi boiler services backed by decades of expertise. Our Gas-Safe registered engineers ensure the use of original parts, offer warranties for all repairs and never charge for call-outs. Whether you’re facing an emergency or need routine service, we provide competitive pricing and dependable maintenance.
- Leaking Worcester Greenstar Boiler Repaired
- Drip in Viesman Vitodens Combi Boiler Repaired
- Ideal Logic Repaired with Loud Noises When Running on Demand
- Repair on Worcester CDI with Heat but No Hot Water
- Boiler Repair Call Out for Loud Noise in Ideal Logic