The customer called to say that their boiler made a strange gurgling sound and cut out after several minutes.
- Marsland Rd, Sale M33 7UE
- Mid Terrace
- Vaillant Eco Tec + Combination Boiler
The boiler breakdown cause was identified as a blocked condensate trap. We carried out a boiler service which included the following:
- Removed the burner case and cleaned out the burner with chemicals and a wire brush. Flushed through with clean water.
- Cleaned out the condensate trap.
- Cleaned the ignition electrodes.
- Air dusted the fan and all visible components and removed dust in the boiler case.
- Checked the burner seal for wear and tear.
- Applied copper grease to the burner retaining nuts.
Advised the customer to have their boiler serviced annually.
A visual inspection and check of the boiler was carried out, followed by a gas safety check and a flue gas analysis.
Manchester Plumbing and Heating (Sale) boiler breakdown service is extremely reliable with our excellent reputation covering the whole Greater Manchester area. We have many years of qualified engineering expertise and experience to back it up. On-going boiler servicing and maintenance ensures the energy efficiency and longevity of your home’s heating system.
- Boiler Leaking in Bungalow in Sale M33 3DF
- Boiler Losing Pressure and Required Topping Up in Sale M33 2LT
- Boiler Malfunctioning with Hot Water in Sale M33 7TS
- No Hot Water from Boiler in Sale M33 7XF